Data Center Overall: 60,000 sq. ft. Raised Floor: 24,800 sq. ft. Office Space: Meeting rooms available on request Site Area: Light industrial Seismic Zone: Low risk Built: 2000
Types: Cage, locking cabinets Standard Rack: 42U x 600 mm x 1000 mm Raised Floor Load: 250 lbs. / sq. ft. Sub Floor Load: 250 lbs. / sq. ft. Cross Connect: Copper, fiber, coaxial Remote Hands: 24x7 Loading Dock: Yes
Electrical Capacity Phase 1: 70W per sq. ft. Phase 2: 98W per sq. ft. Cabinet (1.8, 2.5 Kw) UPS Configuration: N+1 # Utility Feeders: 2 (Supply and standby with auto change over on utility failure) Standby Power Config: Standby Power: 3 x diesel generators; Generator A & B – 3 x 1200 kVA units (2400kVA @ N+1); Generator C – 2 x 1200 kVA units (1200kVA @ N+1); Generator D/E – 3 x 2000 kVA units (4000kVA @ N+1); Diesel Capacity: Fuel Farm – For A,B+C 160,000 Ltrs; Fuel Farm – For D/E 44,000 Ltrs above ground storage tanks
HVAC Distribution: N+1 HVAC System: N+1 Chillers: Hall 1- 15 x 64kW Chilled Water (C/W) = 768kW @ N+3. Hall 2 - 4 x C/W and 3 x D/X = 370kW @ N+1. Hall 3 - 4 x C/W and 3 x D/X = 370kW @ N=1. Hall 4 - 4 x D/X = 159kW @N+1 Hall 5 - 5 x C/W = 252kW @ N+1. Hall 6 - 10 x C/W = 520kW @ N+2. Hall 7 - 3 x C/W = 130kW @ N+1.
Fire Alarm: All halls have VESDA smoke detection with floor and ceiling mounted cross zoned detection Fire Suppression Data Center Areas: FM200 fire suppression. Operation of the gas fire suppression is via “double knock” operation of fire detection with system in manual operation initiation