Data Center Overall: 425,174 sq. ft.
Raised Floor: 33,178 sq. ft.
Office Space: Customer briefing room
Site Area: Light industrial
Seismic Zone: 1
Built: 1966 Retrofitted: 2000
Types: Cage, locking cabinets Standard Rack: 42U x 600 mm x 1000 mm Raised Floor Load: 150 lbs. / sq. ft. Sub Floor Load: 300 lbs. / sq. ft. Cross Connect:
Copper, fiber, coaxial Remote Hands: 24x7 Loading Dock: Yes
Electrical Capacity 75 w/sq. ft. 134 w/sq. ft. Cabinet (2.5 & 5 Kw) UPS Configuration: N+1 Hall 1; 2N other Halls # Utility Feeders: 1 Standby Power Config: N+1 Standby Power: 6 x 4.65MV generators support all Halls except H4 which has 3 x 2MVA generators
HVAC Distribution: N+1, except Hall 4 N+3 HVAC System: Water-cooled CRAC units distribute air through the floor voids Chillers: 6 chillers support halls, three separate chillers support H4
Fire Alarm: VESDA (air sampling) smoke detection and alarm system Fire Suppression Data Center Areas: “Inergen” inert gas is held in a secure central store. Dedicated pipe-work distributes the Inergen to all areas in the event of activation. Operation of the gas fire suppression is a double knock system. The storage capability is designed as N+1. Gas will flood the affected area, which is quickly cleared, after discharge, by gas extract ventilation systems Non-Equipment Areas: Wet sprinkler