Data Center Overall: 167,000 sq. ft.
Raised Floor: 995 sq. ft.
Office Space: None
Site Area: Light industrial
Seismic Zone: 1
Built: 2008 Retrofitted: N/A
Types: Cage, locking cabinets Standard Rack: 42U Raised Floor Load: 999 lbs. / sq. ft. Sub Floor Load: N/A
Cross Connect: Copper, fiber, coaxial
Remote Hands: 24x7
Loading Dock: Yes
Electrical Capacity 137 w per sq. ft. Cabinet (5 Kw) UPS Configuration: 2N # Utility Feeders: 1 Standby Power Config: N+1 Standby Power: Five 2000 Kva diesel generators, 48 hrs of fuel at full load in above ground storage tanks
HVAC Distribution: N+1 HVAC System: Air cooled CRACs Chillers: Independent DX CRACs
Fire Alarm: VESDA (air sampling) smoke detection and alarm system Fire Suppression Data Center Areas: Pre-action dry pipe FM200 Non-Equipment Areas: Wet sprinkler