Data Center Overall: 68,600 sq. ft. Colocation: 40,600 sq. ft. Office Space: Customer drop in cubicles Site: 2-story Site Area: Multi-tenant Seismic Zone: 4 Built: 1982 Retrofitted: 1999
Types: Cage, locking cabinets Standard Rack: 42U Raised Floor Load: None Sub Floor Load: 300 lbs. / sq. ft. Cross Connect: Copper, fiber, coaxial Remote Hands: 24x7 Loading Dock: Yes
Electrical Capacity Bldg. A 150 w/ sq. ft. Bldg. B 150 w/ sq. ft. Cabinet (2.4, 4.3 & 6.2 Kw) UPS Configuration: 2N # Utility Feeders: 2 Standby Power Config: N+1 Standby Power: Bldg. A has three 1,500 kW diesel generators. ***Building A generator #3 is a swing engine and can be used for Building B if needed *** Bldg. B has two 1,600 kw diesel generators; two 16,000 gallon above ground fuel tanks.
HVAC Distribution: N+1 HVAC System: N+1 Chillers: Building A has three 230 Ton air cooled chillers. Building B has four 180 Ton air cooled chillers.
Fire Alarm: VESDA Smoke Detection and Conventional Addressable Fire Alarm System Fire Suppression Data Center Areas: Pre-action dry pipe Non-Equipment Areas: Wet sprinkler