Data Center Overall: 140,654 sq. ft.
Colocation: 92,320 sq. ft.
Office Space: Customer drop in cubicles
Site Area: Business park
Seismic Zone: 1
Built: 2000 Retrofitted: 2008 & 2018
Types: Cage, locking cabinets Standard Rack: 42U & 51U Raised Floor Load: 300 lbs. / sq. ft. Sub Floor Load: 300 lbs. / sq. ft.
Cross Connect: Copper, fiber, coaxial Remote Hands: 24x7
Electrical Capacity Phase I & II - 120 w/sq. ft. Phase III & IV - 200 w/sq. ft. Cabinet (2.4, 4.3 & 6.2 Kw) UPS Configuration: N+1 # Utility Feeders: 2 Standby Power Config: N+1 Standby Power: Six 2,000 Kw diesel generators, five belly tanks and one standalone.
HVAC Distribution: N+1 HVAC System: N+1 Chillers: Eight 400 ton air-cooled chillers. Closed chill water loop with municipal makeup water.
Fire Alarm: VESDA smoke detection and conventional addressable fire alarm system Fire Suppression Data Center Areas: Pre-action dry pipe Non-Equipment Areas: Dry pipe