Data Center Overall: 115,633 sq. ft.
Colocation: 77,124 sq. ft.
Office Space: Customer drop in cubicles
Site Area: Business park
Types: Cage, locking cabinets Standard Rack: 45U Raised Floor Load: 150 lbs. / sq. ft. Sub Floor Load: 300 lbs. / sq. ft.
Cross Connect: Copper, fiber, coaxial Remote Hands: 24x7
Electrical Capacity Cage: 200 w/sq. ft. Cabinet (2.4, 4.3 & 6.2 Kw) UPS Configuration: N+1 # Utility Feeders: 1 Standby Power Config: N+1 Standby Power: Five fuel tanks underground that hold a total of 70,000 gallons of diesel
HVAC Distribution: N+1 HVAC System: N+1 Chillers: Five 600 ton chillers/cooling towers with onsite make-up water
Fire Alarm: VESDA smoke detection and conventional addressable fire alarm system Fire Suppression Data Center Areas: Pre-action dry pipe Non-Equipment Areas: Pre-action dry pipe