Data Center Overall: 137,203 sq. ft.
Colocation: 76,115 sq. ft.
Office Space: Customer drop in cubicles
Built: 1999 Retrofitted: 2005, 2009, 2016
Types: Cage, locking cabinets. Standard Rack: 44U and 45U. Raised Floor Load: 150 lbs. / sq. ft.. Sub Floor Load: 300 lbs. / sq. ft.
Cross Connect: Copper, fiber, coaxial. Remote Hands: 24x7. Loading Dock: Yes
Electrical Capacity Phase I & II – 120 w/sq. ft. Phase III & V – 200 w/sq. ft. Cabinet (2.4, 4.3 & 6.2 Kw) UPS Configuration: 2N # Utility Feeders: 1 Standby Power Config: N+1 Standby Power: Four 2,000 kW and three 2,250 kW diesel generators, three 20,000 gallon underground storage tanks
HVAC Distribution: N+1 HVAC System: N+1 Chillers: Five 600 ton chillers/Two 600 and four 400 ton cooling towers/ Three 30,000 and two 25,000 gallon storage tanks, onsite well for backup of county water
Fire Alarm: VESDA smoke detection and conventional addressable fire alarm system Fire Suppression Data Center Areas: Pre-action dry pipe Non-Equipment Areas: Wet sprinkler